It is currently Mon Nov 28, 2022 9:37 pm

Author Message

 Post subject: Table 410-3 Working Distances?Posted: Tue Feb 24, 2015 1:01 pm

Joined: Tue Apr 08, 2014 12:03 pm
Posts: 8
Hi,
Can someone explain the "T" values given in footnote 1 of Table 410-3 in the 2012 NESC. I am trying to find out if they have an impact on the distance from the arc as one might infer from the language. "...calculated using the MAD... subtracting two times the assumed arc gap length and using the following T values...."

Thanks,
Craig

Top

 Post subject: Re: Table 410-3 Working Distances?Posted: Wed Feb 25, 2015 5:52 am
 Plasma Level

Joined: Wed May 07, 2008 5:00 pm
Posts: 873
Location: Rutland, VT
T is the maximum anticipated per unit overvoltage factor.

_________________
Barry Donovan, P.E.
www.workplacesafetysolutions.com

Top

 Post subject: Re: Table 410-3 Working Distances?Posted: Wed Feb 25, 2015 6:29 am

Joined: Tue Apr 08, 2014 12:03 pm
Posts: 8
Hi Barry,
Thank you for the response and information. I would assume that if we want determine that other transient voltage levels should be used then we would need to analyze the system for such rather than using the default values.

Craig

Top

 Post subject: Re: Table 410-3 Working Distances?Posted: Wed Feb 25, 2015 9:37 am
 Arc Level

Joined: Tue Jan 13, 2009 5:00 pm
Posts: 596
The T values were used in calculating the MAD, see Table 441-1. I expect the NESC T values and MADS should be conservative enough. In any case, you can only increase the MAD. Also note that if you use a larger MAD to calculate the distance to the arc, the result will be less conservative than what's in Table 410-3.

Top

 Post subject: Re: Table 410-3 Working Distances?Posted: Wed Feb 25, 2015 10:12 am

Joined: Tue Apr 08, 2014 12:03 pm
Posts: 8
Hi Steven,
Thanks for the added reference. I can see that T values are TOV values. and I understand what you are saying with regards to less conservative results coming from increased MAD's but I think that when using in the NESC option for analysis in my software (CYME) the working distance is determined form me based on voltage level and the default T values given in the NESC.

Craig

Top

 Display posts from previous: All posts1 day7 days2 weeks1 month3 months6 months1 year Sort by AuthorPost timeSubject AscendingDescending
 Page 1 of 1 [ 5 posts ]

 All times are UTC - 7 hours

 You cannot post new topics in this forumYou cannot reply to topics in this forumYou cannot edit your posts in this forumYou cannot delete your posts in this forumYou cannot post attachments in this forum

 Jump to:  Select a forum ------------------ Forum Library / Articles The Lounge    Question of the Week - What Do You Think?    Arcflashforum.com Feedback and Announcements    Off Topic Discussions    News in Electrical Safety Arc Flash and Electrical Safety    General Discussion    Electrical Safety Practices    Equipment to Reduce Arc Flash Dangers    Personal Protective Equipment (PPE) Arc Flash Studies    General Discussion    Arc Flash Labels    Software for Arc Flash Studies    System Modeling and Calculations    NEW! Electrode Configuration Library â 2018 IEEE 1584 Codes and Standards    CSA Z462 Workplace Electrical Safety    EAWR Electricity at Work Regulations, HSE - Europe    OSHA CFR Title 29    IEEE 1584 - Arc-Flash Hazard Calculations    NFPA 70 - National Electrical Code - NEC (R)    NESC - ANSI C2 - National Electrical Safety Code    NFPA 70E - Electrical Safety in the Workplace    2015 NFPA 70E Share It Here    Arc Flash Photos    Your Stories    What's Wrong Here? by Joe Tedesco
© 2022 Arcflash Forum / Brainfiller, Inc. | P.O. Box 12024 | Scottsdale, AZ 85267 USA | 800-874-8883