It is currently Tue Nov 29, 2022 1:47 pm

Author Message

 Post subject: Hrc vs atpv ??Posted: Tue Oct 19, 2010 4:16 pm

Joined: Tue Oct 19, 2010 4:01 pm
Posts: 8
I am just getting started in this and my company has already done a study. Most of our equipment is marked but with a ATPV value not in HRC. My question, is a easy table to convert one to the other. Some tables say that HRC 2 for example is a min of ATPV 8. Is this the lower limit of a HRC 2 or is it the upper limit? Does HRC 2 go from 4 to 8 or 8 to 25? Tried reading thru 70E and it does not seem to be clear to me.

Top

 Post subject: Posted: Wed Oct 20, 2010 6:37 am
 Arc Level

Joined: Mon Jan 18, 2010 11:35 am
Posts: 554
Location: Wisconsin
Look at Table 130.7(C)(11).

It provides the minimum ATPV rating per HRC.
For your example: HRC2 requires clothing with a minimum Arc Rating (ATPV) of 8 cal/cmÂ².

Top

 Post subject: Posted: Wed Oct 20, 2010 11:30 am
 Sparks Level

Joined: Wed Oct 29, 2008 6:06 am
Posts: 136
Location: Michigan
elecfx wrote:
I am just getting started in this and my company has already done a study. Most of our equipment is marked but with a ATPV value not in HRC. My question, is a easy table to convert one to the other. Some tables say that HRC 2 for example is a min of ATPV 8. Is this the lower limit of a HRC 2 or is it the upper limit? Does HRC 2 go from 4 to 8 or 8 to 25? Tried reading thru 70E and it does not seem to be clear to me.

The Arc Thermal Performance Value (ATPV) is presented in calories per square centimeter and represents the maximum capability for arc-flash protection of a particular garment. This value is usually sewn onto the outside of the garment in large letters. If your company has done an arc flash hazard analysis and the equipment label displays the ATPV you need to wear FR clothing that is rated that many cal/cm2 or higher.

If you want to relate a given ATPV to a HRC I would do so as follows:

HRC 0 = 0 - 1.1 cal/cm2
HRC 1 = 1.2 - 4 cal/cm2
HRC 2 = 4.1 - 8 cal/cm2
HRC 3 = 8.1 - 25 cal/cm2
HRC 4 = 25.1 - 40 cal/cm2

If you are not performing an arc flash hazard analysis and youâre instead following T130.7(C)(9) then the PPE is assigned based on task and voltage level, not the calculated incident energy (IE). Since the IE is unknown when an analysis is not done, these tasks are assigned a Hazard Risk Category (HRC). The HRC then dictates the minimum PPE ATPV which must be worn when using this method to determine PPE; see T130.7(C)(11).

HRC 0 = N/A
HRC 1 = 4 cal/cm2
HRC 2 = 8 cal/cm2
HRC 3 = 25 cal/cm2
HRC 4 = 40 cal/cm2

Another thread on this topic to check out:

Top

 Post subject: Posted: Wed Oct 20, 2010 3:21 pm

Joined: Tue Oct 19, 2010 4:01 pm
Posts: 8
Thanks A King, I think that is where I was getting confused. I was trying to use both at the same time to figure out what was the right PPE to put on.

I also read the link, I think, although good discussion, people are forgeting that what the code states is a mininum, you must do atleast this. They are not stating that you cannot do both just that you must make sure that the hazard is clearly stated in form "A" or "B". I just received a 70E handbook, I looked this up and the blue explaintion is just as I was thinking.

Top

 Display posts from previous: All posts1 day7 days2 weeks1 month3 months6 months1 year Sort by AuthorPost timeSubject AscendingDescending
 Page 1 of 1 [ 4 posts ]

 All times are UTC - 7 hours

 You cannot post new topics in this forumYou cannot reply to topics in this forumYou cannot edit your posts in this forumYou cannot delete your posts in this forumYou cannot post attachments in this forum

 Jump to:  Select a forum ------------------ Forum Library / Articles The Lounge    Question of the Week - What Do You Think?    Arcflashforum.com Feedback and Announcements    Off Topic Discussions    News in Electrical Safety Arc Flash and Electrical Safety    General Discussion    Electrical Safety Practices    Equipment to Reduce Arc Flash Dangers    Personal Protective Equipment (PPE) Arc Flash Studies    General Discussion    Arc Flash Labels    Software for Arc Flash Studies    System Modeling and Calculations    NEW! Electrode Configuration Library â 2018 IEEE 1584 Codes and Standards    CSA Z462 Workplace Electrical Safety    EAWR Electricity at Work Regulations, HSE - Europe    OSHA CFR Title 29    IEEE 1584 - Arc-Flash Hazard Calculations    NFPA 70 - National Electrical Code - NEC (R)    NESC - ANSI C2 - National Electrical Safety Code    NFPA 70E - Electrical Safety in the Workplace    2015 NFPA 70E Share It Here    Arc Flash Photos    Your Stories    What's Wrong Here? by Joe Tedesco
© 2022 Arcflash Forum / Brainfiller, Inc. | P.O. Box 12024 | Scottsdale, AZ 85267 USA | 800-874-8883