It is currently Fri Sep 18, 2020 10:11 pm

Author Message

 Post subject: Table H.4Posted: Thu Jan 19, 2012 7:23 am

Joined: Mon Jul 06, 2009 11:39 am
Posts: 3
As I understand the application of these Tables, I should only use 8 cal or 40 cal PPE within the limits stated in the Table for the system voltage and the maximum three-phase bolted fault current.

Does not an incident energy calculation yield energy levels below the Table values for 8 cal and 40 cal PPE?

Is there a feature I am not recognizing?

Top

 Post subject: Posted: Thu Jan 19, 2012 2:46 pm

Joined: Wed Aug 01, 2007 4:05 pm
Posts: 11
If the calculations show an incident energy up to 8 cal,then use 8 cal. If the Ei is between 8 and 40 cal, then use 40 cal. It's a 2 category approach. The problem is if you Ei above 8 is only 10 or 15 cal, going all the way to 40 might be a bit much. Especially in the summer.

Top

 Post subject: Posted: Sat Jan 21, 2012 8:21 am

Joined: Mon Jul 06, 2009 11:39 am
Posts: 3
If the results of an arc flash hazard analysis were that the incident energy was 7.5 cal but the available bolted fault current exceeded the values, at the system voltage, in Table H.4 would it still be acceptable to use 8 cal PPE?

Top

 Post subject: Posted: Sun Jan 22, 2012 8:02 am
 Plasma Level

Joined: Tue Oct 26, 2010 9:08 am
Posts: 2174
Location: North Carolina
SRW wrote:
If the results of an arc flash hazard analysis were that the incident energy was 7.5 cal but the available bolted fault current exceeded the values, at the system voltage, in Table H.4 would it still be acceptable to use 8 cal PPE?

1. If the available bolted fault exceeds the tabular result, then you can't use the tabular results because you violated the assumptions.
2. If you did the analysis, then tabular results don't matter anyways. You use the actual calculated result.
3. The PPE tables even with the "4 level' system (0-4) are not intended to apply to actual arc flash hazard calculations anyways. Those are intended for use with the other tables.

With that out of the way, we can get down to discussing PPE if you have actually calculated your incident energy:
1. In practice, most people read those tables and apply their calculated incident energies to the tabular results just because it is a convenient way to determine required PPE. As long as the PPE specified exceeds the incident energy calculated, then it is sufficient. Note that some manufacturers actually specify a higher cal/cm^2 value for their PPE and give both ratings (ATPV and tabular PPE rating). Since you used the calculation method, you can use either value. The actual ATPV value will be higher.
2. Since you have calculated values, there is nothing stopping you from implementing as many or as few "levels" as you desire. Two examples:
A. Many companies have a "2" level system; 1.2 cal/cm^2 and 40 cal/cm^2. They don't bother with the ones in between, including the one I currently work for. There are practical problems with doing this for electricians though so you may want to add a third level.
B. Along the same lines, many go for 1.2, 8, and 40 cals/cm^2 as suggested in the appendix, although often the "8" level becomes more like 10-12 depending on the PPE manufacturer. The reason for picking "8" instead of "4" is because 12 oz cotton treated with the ammonia "FR" process almost automatically yields around an 8-12 cal/cm^2 ATPV. The only fundamental PPE difference between 4 and 8 cal/cm^2 is the inclusion of the balaclava or some sort of hood which was a recent (2009) addition.
C. I (and others) have also implemented another variation on the 2 level system in the past: 4, and 40. Especially in a glass, welding, or iron/steel industry shop, FR clothing is usually mandatory to begin with. Except for the balaclava or hood, the minimum standard work wear is already 4 cal/cm^2, so 1.2 cal/cm^2 is not even a consideration. It is also very easy to make a 3 level system (4/8/40) with minor additional PPE requirements.

There is also nothing stopping you from "mixing it up" in terms of using these simplified approaches with the tabular approach. Regardless of how you determine the "levels" to be used, the fundamental rule is that the PPE to be worn must equal or exceed the available incident energy level if PPE is required. The determination of whether or not PPE is required depends on your risk assessment, and that in turn depends on the task to be done, as made abundantly clear by all the references to looking at electrical hazards on a task-by-task basis in the 2012 edition of 70E.

Top

 Post subject: Posted: Mon Jan 23, 2012 6:26 am

Joined: Wed Aug 01, 2007 4:05 pm
Posts: 11
Great Response Paul, Thanks!

Top

 Display posts from previous: All posts1 day7 days2 weeks1 month3 months6 months1 year Sort by AuthorPost timeSubject AscendingDescending
 Page 1 of 1 [ 5 posts ]

 All times are UTC - 7 hours

 You cannot post new topics in this forumYou cannot reply to topics in this forumYou cannot edit your posts in this forumYou cannot delete your posts in this forumYou cannot post attachments in this forum

 Jump to:  Select a forum ------------------ Forum Library / Articles The Lounge    Question of the Week - What Do You Think?    Arcflashforum.com Feedback and Announcements    Off Topic Discussions    News in Electrical Safety Arc Flash and Electrical Safety    General Discussion    Electrical Safety Practices    Equipment to Reduce Arc Flash Dangers    Personal Protective Equipment (PPE) Arc Flash Studies    General Discussion    Arc Flash Labels    Software for Arc Flash Studies    System Modeling and Calculations    NEW! Electrode Configuration Library – 2018 IEEE 1584 Codes and Standards    CSA Z462 Workplace Electrical Safety    EAWR Electricity at Work Regulations, HSE - Europe    OSHA CFR Title 29    IEEE 1584 - Arc-Flash Hazard Calculations    NFPA 70 - National Electrical Code - NEC (R)    NESC - ANSI C2 - National Electrical Safety Code    NFPA 70E - Electrical Safety in the Workplace    2015 NFPA 70E Share It Here    Arc Flash Photos    Your Stories    What's Wrong Here? by Joe Tedesco
© 2019 Arcflash Forum / Brainfiller, Inc. | P.O. Box 12024 | Scottsdale, AZ 85267 USA | 800-874-8883