It is currently Mon Sep 27, 2021 6:16 am

Author Message

 Post subject: Units (for inputs) in IE calcs for capacitors (70E-2021)Posted: Thu Aug 26, 2021 10:46 am

Joined: Tue May 22, 2012 12:08 am
Posts: 12
In Annex R of NFPA 70E-2021, equations are defined for calculating Incident Energy (open air) which are labelled R.9.1a & R.9.1b. In the explanation of the inputs, no units are given. I presume the following are correct (as these units were used in the earlier stored energy equation, R.8.2)...
• E = joules
• V = volts

There is also another input, radius (r), which presumably corresponds to working distance and is therefore specified in millimetres or centimetres rather than inches?

Top

 Post subject: Re: Units (for inputs) in IE calcs for capacitors (70E-2021)Posted: Wed Sep 01, 2021 3:42 pm
 Plasma Level

Joined: Mon Sep 17, 2007 5:00 pm
Posts: 1620
Location: Scottsdale, Arizona
This could have been written with more clarity.

It appears that C is total capacitance in farads as shown in equations such as R.8.2 and R.8.3c.

However for voltage V it depends on which equation is used. R.8.2 defines V as peak voltage where as R.8.3c defines V as phase-to-phase voltage rms.

Further information is found in R8.4 Voltage. For peak voltage, the voltage applied across the capacitors that would cause the maximum charge should be used. For disconnected capacitors in storage or for disposal, the capacitor rated voltage should be used.

I agree this is not clear and can be confusing as written.

Top

 Post subject: Re: Units (for inputs) in IE calcs for capacitors (70E-2021)Posted: Mon Sep 13, 2021 8:07 am

Joined: Tue May 22, 2012 12:08 am
Posts: 12

I'm not sure if you saw the question at the bottom of my initial post and are able to clarify units for Radius...

Radius (r) is another input in the Incident Energy equations [R.9.1a] and [R.9.1b], which presumably corresponds to working distance and is therefore specified in millimetres or centimetres rather than inches?

Top

 Display posts from previous: All posts1 day7 days2 weeks1 month3 months6 months1 year Sort by AuthorPost timeSubject AscendingDescending
 Page 1 of 1 [ 3 posts ]

 All times are UTC - 7 hours

 You cannot post new topics in this forumYou cannot reply to topics in this forumYou cannot edit your posts in this forumYou cannot delete your posts in this forumYou cannot post attachments in this forum

 Jump to:  Select a forum ------------------ Forum Library / Articles The Lounge    Question of the Week - What Do You Think?    Arcflashforum.com Feedback and Announcements    Off Topic Discussions    News in Electrical Safety Arc Flash and Electrical Safety    General Discussion    Electrical Safety Practices    Equipment to Reduce Arc Flash Dangers    Personal Protective Equipment (PPE) Arc Flash Studies    General Discussion    Arc Flash Labels    Software for Arc Flash Studies    System Modeling and Calculations    NEW! Electrode Configuration Library – 2018 IEEE 1584 Codes and Standards    CSA Z462 Workplace Electrical Safety    EAWR Electricity at Work Regulations, HSE - Europe    OSHA CFR Title 29    IEEE 1584 - Arc-Flash Hazard Calculations    NFPA 70 - National Electrical Code - NEC (R)    NESC - ANSI C2 - National Electrical Safety Code    NFPA 70E - Electrical Safety in the Workplace    2015 NFPA 70E Share It Here    Arc Flash Photos    Your Stories    What's Wrong Here? by Joe Tedesco
© 2019 Arcflash Forum / Brainfiller, Inc. | P.O. Box 12024 | Scottsdale, AZ 85267 USA | 800-874-8883