125 kVA – Going, going, gone! After much speculation about the fate of the 125 kVA transformer “exception”, the 2018 Edition of IEEE 1584 – IEEE Guide for Performing Arc-Flash Hazard Calculations has finally been published and made it official. The 125 kVA transformer exception has been deleted!
In its place is the new language:
“Sustainable arcs are possible but are less likely in three-phase systems operating at 240 V nominal or less with an available short circuit current below 2000A”Continue reading →
One sentence in the IEEE 1584 Standard, IEEE Guide for Performing Arc-Flash Hazard Calculations, frequently has people scratching their heads: Equipment below 240V need not be considered unless it involves at least one 125 kVA or larger low-impedance transformer in its immediate power supply. What does this sentence mean? What is so significant about 240 volts and 125 kilovolt-amperes?
About Jim Phillips: Electrical Power and Arc Flash Training Programs – For over 30 years, Jim Phillips has been helping tens of thousands of people around the world, understand electrical power system design, analysis, arc flash and electrical safety.
Jim is Vice Chair of IEEE 1584, International Chairman of IEC TC78 Live Working and Steering Committee Member – IEEE/NFPA Arc Flash Collaborative Research Project. He has developed a reputation for being one of the best trainers in the electric power industry.Learn More
Arc Flash & Electrical Power Training Classes by Jim Phillips Click Here
Arc Flash & Electrical Power Training Productsby Jim PhillipsClick Here
Sign-up for my monthly publication “Grey Matter” which contains news about new standards, conferences, technical articles, Electrical Engineering news and more! Click Here
HEY! You CAN'T learn from a pop-up
But you CAN learn from Jim's Grey Matter!
Join thousands of your colleages and "fill your brain" with Jim Phillips' monthly Grey Matter containing technical articles, news about new standards as well as information about new videos and training classes.